Standard Secondary Voltage
600 Volts, 10Kv BIL Full Wave.
+/-1% at all burdens up to 5 VA at 1.0 and 0.95 P.F.
40 VA @ 30 C. amb.; 27 VA @ 55 C. amb.
Terminals are No. 6-32 binding head screws and cup washer. (Note: All transformers listed with the exception of the 480v and 600v are ANSI C 57.13 group 1. The 480v and 600v are group 2.)
1 Year Warranty
These transformers are encased in a thermoplastic case with the core and windings encapsulated in resin. They are designed for line-to-line operation but may also be used in line-to-neutral or line-to-ground configuration at 58% of rated voltage. It is recommended that a 0.40 Amp fuse be used in the secondary to protect the transformer.